Please use this identifier to cite or link to this item:
|Title:||Cfd simulation of spray dehumidification process in moist air||Authors:||Farnoud, A.
|Issue Date:||2014||Publisher:||Begell House Inc.||Abstract:||This study presents a two dimensional numerical investigation of interaction between hot humid air and sub-cooled water which is sprayed contrary to the airflow direction. The droplet evaporation and condensation are analyzed using ANSYS-FLUENT commercial software. Diameter of water droplets are chosen between 8 µm and 12 µm and mass flow rates are in the range of 2.5 g/s and 4 g/s. Analysis predict that droplet transport and evaporation depend on droplet diameter and mass flow rate of the water-spray. By decreasing the droplet size more evaporation and condensation is achieved, and as a result, more heat is released. It is also shown that increasing mass flow rate of the water spray leads to heat transfer enhancement and reduction of humidity. © 2014, Begell House Inc. All rights reserved.||Description:||International Symposium on Convective Heat and Mass Transfer, CONV 2014 -- 8 June 2014 through 13 June 2014 -- 268949||URI:||https://doi.org/10.1615/ICHMT.2014.IntSympConvHeatMassTransf.100
|Appears in Collections:||Scopus İndeksli Yayınlar Koleksiyonu / Scopus Indexed Publications Collection|
Show full item record
Items in GCRIS Repository are protected by copyright, with all rights reserved, unless otherwise indicated.